Add Products to the Cart to Obtain Instant Discounts!
April 05, 2021 0 Comments
Selecting the correct chemical injection pump can be challenging because of the variations and types of chemical injection pumps available. To pick the best injection pump for the application you’ll need to consider several factors.
This is probably the most important question, because certain materials of construction will work well with specific chemicals and this will determine the wet end of the pump. The concentration is also important because materials that would normally work well at lower concentrations may not perform well at higher concentrations. Material Compatibility Chart
You want to choose a pump that runs at approximately 70%-80% of its total capacity in a normal operational situation. This is the “sweet spot” where chemical pumps will be most accurate and maintain prime. There are other applications that may require a broad range of outputs, so pumps that can be accurately turned down to provide low outputs are desired. Wide variation in flow especially in the 5%-25% range are best served by pumps that have adjustable motor speeds, because they can vary the time it takes to complete a stroke, much like slowly depressing a syringe.
This is a critical question, because pumps are rated at a maximum discharge pressure and when that line pressure exceeds the discharge pressure of the chemical injection pump, little or no chemical will be injected. Alternately, if a chemical pump is rated at a much higher discharge pressure, it can cause an overfeed of chemical due to inertia, the check balls will not seat immediately and the chemical will continue to pass after the stroke is completed.
There are three common modes of control: manual, digital pulse and analog input. Manual is simple control based on manually adjusting stroke length and frequency to obtain the desired flow rate. Digital pulse is a discrete contact or optical signal that can be read by the control module and converted to strokes per minute. Many chemical pumps have multipliers and dividers for the discrete contacts, allowing greater flexibility in the output range proportional to the pulse signal. Analog control is typically a 4-20 milliamp signal, which varies the stroke frequency in a linear fashion proportional to the output of the device, such as a flowmeter or controller. For example, a pH controller may be set to pH 7 which is equal to 4 mA and pH 9 is equal to 20 mA. The pump has 0-360 strokes per minute. A pH of 8 would be the middle of the scale equal to 12 mA and the pump would be running at 180 strokes per minute.
Most chemical metering pumps are not meant to be put in direct sunlight with elevated temperatures or direct rain. While the pump may work fine for a while, this will greatly decrease the longevity of the pump. It is always good practice to shield the pump with a protective housing or cover when out in the elements.
There are different ratings for environmental resistance, typically designated by an IP or NEMA rating. These ratings will help you to determine if your pump is correct for your application, for example, an IP 67 rated chemical pump would have significant resistance to hose-downs and flooding.
Viscosity is the resistance to flow of a particular chemical. An example of a high viscosity fluid is honey. High viscosities have a tendency to keep the check balls suspended, which will reduce output or cease output altogether. Metering pumps have limitations on viscosity based on their design. Some designs utilize springs in the check valves to create pumps with higher viscosity capabilities. Viscosity often changes with temperature, so it is important to maintain the temperature of the solution to stay within the specifications of the chemical pump or be sure that the pump can handle the maximum viscosity at a specific temperature where it will be used.
Many oxidizers such as sodium hypochlorite, hydrogen peroxide, peracetic acid and bromine evolve gas that can be a serious issue to positive displacement pumps. Many times peristaltic pumps have been used because they do not compress the same void continuously (similar to vapor lock), however, many low price peristaltic pumps do not have the desired pressure requirements, accuracy and repeatability. New innovations by chemical injection pump manufacturers have resolved most of these issues with diaphragm pumps by monitoring the flow with magnetic or ultrasonic flow meters that feedback to the control module of the pump. When the flow drops below a specified output, the pump speeds up to eject the gas through an auto-degassing valve and maintains prime.
Manufacturers tout the features of their chemical injection pumps as being the most innovative and necessary, but as the consumer you must determine what the application requires and how critical those features are to you. Not every application requires a magnetic flow meter and software that controls the loss of prime, but if you are feeding sodium hypochlorite to a drinking water supply at an unmanned facility, these features are critical. Repeatability and reliability are probably the most important functions of the pump. You should be able to measure the output of the pump when installed and again in 3 months and have the same value. If not, then you will always be chasing your desired residual and continually adjusting the pump.
We Simplify the selection process by placing the core information first. No need to read through all the meaningless buzz words. Just look at the important information and decide if the pump is the one you need!
You can read the original article @ https://www.rhfs.com/pulse/how-to-choose-the-right-metering-pump/
April 28, 2021 0 Comments
Most people have heard of ozone thanks to media coverage about pollution and the ozone layer. But for many, that is where their knowledge ends. The first thing you should tell a homeowner is that ozone is nothing more than O3—three oxygen atoms bound together.
That extra oxygen atom wants to hook up with other material, like unwanted microorganisms in water filtration systems. For the purpose of disinfecting water, ozone comes in contact with contaminants and pathogens that can damage equipment and get in the water supply. The extra oxygen atom oxidizes the contaminant and the O3 becomes O2—just plain old oxygen.
April 28, 2021 0 Comments
It was shown that after 30 seconds of in vitro direct exposure to ozone, 99 percent of the viruses are inactivated. Although this evidence is of considerable importance, outside of the laboratory models, there are various parameters that influence the time required to obtain the same result. First of all, it was seen that the inactivation of 99% of viruses by ozonation requires its spread at concentrations higher than those necessary for the bacteria. A longer exposure time, about 30 minutes, is necessary for the treatment of the surfaces of the environment (surface viruses), while for any viral particles suspended in the air (airborne viruses) 8-10 minutes are enough to remove 99.9% of them. Viruses in water are more susceptible to ozone inactivation and short contact time, about 1 min or little more, are sufficient to inactivate 99% of them.
April 27, 2021 0 Comments
A positive displacement pump moves a fluid by repeatedly enclosing a fixed volume, with the aid of seals or valves, and moving it mechanically through the system. The pumping action is cyclic and can be driven by pistons, screws, gears, lobes, diaphragms or vanes. There are two main types: reciprocating and rotary.Positive displacement pumps are preferred for applications involving highly viscous fluids such as thick oils and slurries, especially at high pressures, for complex feeds such as emulsions, foodstuffs or biological fluids, and also when accurate dosing is required.